|AT series||MT series|
|Total thickness||1000LB(< 2.5mm depression)||2500LB|
|Anti-static vinyl wear layer||5.0 mm||5.0 mm|
|Transparency pure PVC wear layer||1.0 mm||-|
|Multi-layer vinyl backing||-||0.5 mm|
|Glass fiber reinforcement back||yes||yes|
|Total weight per sq. meter||9.2 kg||9.2 kg|
|Performance||AT series||MT series||Method|
|Electrostatic propensity||less than 0.6 kv||less than 2.0 kv apply anti-static wax)||AATCC 134-01|
|Fire resistance index||class 1||class 1||NFPA 253 / ASTM E-648|
|Dimension stability||< 0.15%||< 0.07%||ASTM F2199|
|Anti-slip (coefficient of friction)||-||< 0.99 (dry)
< 0.78 (wet)
|Taber wear test < 0.007 mm loss||500 cycles||12,500 cycle||ASTM D4060|
|Chemical resistance||no change||no change||24 hours ratings ASTM F925-02|
|Static Load||< 2.0% compression||< 1.5% compression||ASTM F970-00|
|Color fastness to light||no change - rating 5||slight change - rating 4||AATCC 16-03|
|Special run color||minimum 500 sq. meters (5,380 sq. feet)||-|
|Packing||8 pieces per box||8 pieces per box||-|
|Color variation||Colors may vary due to different production lot||-|
AT series: to maintain anti-static property, do not apply oil-base wax.
MT series: anti-static wax shall be applied at areas where electrostatic propensity <2.0 kv is required.
Sand and alien materials should be removed. They may cause damage.Keeping floor clean is necessary in order to maintain steady anti-static property.
General clean by damp mop only. In case of badly contaminated spots, apply diluted mild detergent only at the contaminated spots, and brush. The contaminated spots can be cleaned easily. The detergent should be removed by damped mop at least twice.
Waxing: AT series: use water-base emulsion wax only. Waxing after floor clean and dry. MT series: use anti-static wax. Wax after floor clean and dry.